Order On-line Tracking
It is suitable for power grid with rated voltage 0.6/1kV or the power transmission in the power equipment.
The highest environment permissible continuous operating temperature for the conductor of the PVC Insulating Power Cable to work normally is 90℃. In case of short circuit (with duration less than 5 seconds), the highest temperature of the conductor is less than 250℃.
The ambient temperature under installation should not be below 0℃.
The recommended bending radius: for mono-core cable, not less than 20 times of the cable's actual external diameter; for multi-core cable, not less than 15 times of the cable's actual external diameter.
Cable operation condition：Cable operation condition：
6.1 The single-core cables are parallel laid, the distance between the cable center is 2 times of the cable diameter for cross-section area of conductor≤185185mm2 and 90mm for cross-sectional area of conductor≥240mm2.
6.1Ambient air temperature: 40℃.
6.1 Max. continuous operating temperature of conductor: 90℃.
6.2 Direct in the ground
6.1 The single-core cables are installed separately, the distance between the cable center is 2 times of the c ccable diameter.
6.1 Soil temperature: 25℃.
6.2 Max. continuous operating temperature of conductor: 90℃.
6.2 Thermal resistively of soil: 1.0℃.m/W.
6.2 Depth of laying: 0.7m.
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|