||Low and Medium Voltage Cable|
||Standard Export Drum |
||IEC, ASTM, BS, DIN, AS |
||Henan, China |
1. Used as power transmission & distribution
2. Std: IEC, BS, DIN, NFC, ASTM etc
3. Make up: CU, PVC insulate
The electrical cable(electric cable) is mainly have 2 kinds listing as followings:
1. The PVC insulated PVC sheath power electric Cable
The conductor can be copper or aluminium; Be strands, solid, flexible
The insualtion is PVC
The Jacket/Sheath is PVC
Armored or without armored
Armoured material: Can be steel tape(sta) or steel wire(swa) or others as your request!
The recommended nominal cross section is from 1.5 sq mm to 630 sqmm
The core number can be single or multi
The Voltage is 0.6/1kV
The long-time working temperature of cable should not be higher than 70 celsius
When core is in short-circuit(max 5s) the temperature should not be exceed 160 celsius
While installation the ambient temperature should not be lower than 0 celsius
|PVC insulated PVC sheathed power cable
|Can be laid at indoor, tunnel and tube .Cable cannot under take mechanism outside force|
|PVC insulated and PE sheathed power cable
|Can be laid at indoor, tunnel tube and serious polluted places. Cable cannot undertake mechanism outside force|
|PVC insulated steel belt armored and PVC sheathed power cable
|Can be laid at indoor, tunnel tube and mining well. Cable cannot undertake mechanism outside force|
|PVC insulated steel belt armored and PE sheathed power cable
|Can be laid at indoor, tunnel tube mining well and serious polluted places. Cable cannot undertake mechanism outside force|
|PVC insulated fine steel wire armored PVC sheathed power cable
|Can be laid at indoor, underground and mining well .Cable can undertake mechanism outside force|
|PVC insulated fine steel wire armored PE sheathed power cable
|Can be laid at indoor, underground .Cable can under take mechanism outside force|
|PVC insulated thick steel wire armored PE sheathed power cable
|Can be laid at indoor, underground,mining well .Cable can under take mechanism outside force|
|PVC insulated fine steel wire armored PVC sheathed power cable
|Can be laid at indoor, underground ,mining well and the places of be terrible polluted. Cable can under take mechanism outside force|
- Q:How to effectively reduce the cost of car wiring harness?
- 5mm, that is 100: 76 followed by the proportion of push The height of the isosceles triangle at the time of the bend of the 200 high bridge is also suitable for the adjustment of the 90 ° bend; the use of the tool is cut off and the bending of the bridge is 90 ° Bridge elbow As for the length of the bridge to limit the restructuring of the elbow, as long as the use of junior high school learned by the simple mathematical knowledge of the calculation, any length distance can be controlled The use of mathematical methods simple calculation, a variety of angles, the length of the elbow can be made zuo
- Q:The wall was sideways opened a trough how to do ah?
- With steel wire, lead the bend round, but do not let the wire can hold the pipe wall, and sometimes also need two twisted wire, wire over the past OK
- Q:What does ZR-YJV 6mm2 * 3 cable mean?
- The initial also said that car 3S brand stores, mainly refers to the front of the three S
- Q:The telephone line, TV line, cable, power lines are worn to a wire tube, what will happen?
- VV06 / 13X185 + 1X95 copper core PVC insulated PVC sheathed power cable Reference Price: low voltage power cable VV06 / 13X185 + 1X95 latest price 【2015-06-03】 Specifications: 3X185 +1X95 Conductor technology: B-3; red this price: 34195 yuan / m; monitoring price: 28502 yuan / m VV2206 / 13X185 + 1X95 copper core PVC insulated steel tape armored PVC sheathed power cable reference Price: low voltage power cable VV2206 / 13X185 + 1X95 latest price 【2015-06-03】 Specifications : 3X185 + 1X95; conductor technology: B-3; red price: 35041 yuan / m; monitoring price: 37734 yuan / m YJV06 / 13X185 + 1X95 copper core XLPE insulated PVC sheathed power cable Reference Price: low voltage power cable YJV06 / 13X185 + 1X95 latest price 【2015-06-03】 Specifications: 3X185 + 1X95 conductor technology: B-3; red price: 34084 yuan / m; monitoring price: 28477 yuan / m YJV2206 / 13X185 + 1X95 copper core XLPE insulated steel tape armored PVC sheathed power cable Reference Price: low voltage power cable YJV2206 / 13X185 + 1X95 latest price [2015-06-03] Specifications: 3X185 +1X95; conductor technology: B-3; red price: 34900 yuan / m; monitoring price: 37573 yuan / m Note: Conductor technology: B-3 stranded shaped conductor (such as fan); monitoring price is the latest reference price Quote data from: "cable (dianlancn)" network - the network red price
- Q:How long is the service life of the cable?
- cable bridge and other pipes and other facilities shall not share a column (bracket)
- Q:Ask you a question: how the computer CD-ROM power supply 5V and 12V two lines? Another audio and video cable which group?
- Cable bridge at both ends to be installed across the ground wire, ground wire diameter can not be less than 16mm2. Wire ends and wire ends of the middle box to be installed at both ends of the ground wire, grounding wire diameter can not be less than 6mm2. Full length bridge with the grounding system connected to not less than 2. Cable bridge is divided into trough, tray and ladder-type, mesh and other structures, by the bracket, arm and installation accessories and other components. Can be set up independently, can also be attached to a variety of structures (structures) and corridor stent, reflecting the structure is simple, handsome in appearance, flexible configuration and easy maintenance features, all parts are required galvanized, installed in the building Outside the bridge, if it is in the vicinity of the sea or belong to the corrosion area, the material must have anti-corrosion, moisture resistance, good adhesion, high impact resistance of the physical characteristics. According to the relevant provisions of the specification, galvanized cable bridge for a good grounding. galvanized cable tray direct board each fixed bolt contact resistance should be less than 0.005Ω, then the cable bridge can be used as a ground trunk (dusting cable tray should not be used as a grounding line), the resistance of each cable bridge can be the following formula Calculate: r = ρ · L / S where: ρ = 15 × 10Ω-6 / cm (20 ℃); L = length calculated by 100mm; S = cross-sectional area of cm2. The unit resistance value of the ladder on the pallet is shown in Table 2. The unit resistance value of the cable duct is shown in Table 3 The resistance of each ladder (or each cable slot) after the installation of the cable tray is the total: R = R (r + 1 / 3r ') where: R - ladder, that is, (cable trough) total length of the total resistance (mΩ); r - ladder unit length resistance (mΩ / m)
- Q:What is the cable for the YJV33 cable?
- If there is a mutation in the target fragment, all the dideoxy-terminated fragments that are larger than a certain size corresponding to the mutant position have no wild-type system, and the rate of detection of mutations is improved for each occurrence of multiple changes in the mobility The ddF method overcomes the difficulty of SSCP analysis due to the effect of DNA length on SSCP, and produces a specific single stranded DNA by a dideoxycyclic acid to show that the DNA fragments with suitable length indicate SSCP changes
- Q:Power cable yjv22-10kv-3 * 50 what it means
- Yj is cross-linked polyethylene insulation, v PVC sheathed 22 is double steel tape armored, voltage 10KV, 50 square three-core copper cable
- Q:What kind of material should be selected for the fixing bracket of the cable trunking
- General 2.5 square wire load is 2 kilowatts, and rubber sheathed cable, full load can reach 3 kilowatts are no problem (estimated again, it is not safe). The load level of the wire is mainly dependent on the current, but also on the voltage level. Under normal circumstances 50A below 1 square millimeter safe carrying capacity is 6A, 50 ~ 100A current 1 square millimeter of the safe carrying capacity is 5A, 100A current above the general take 1 square millimeter of the safe current is 2.5A; so many large square copper cable You can calculate the current. According to the three-phase alternating current formula: P = 1.732 * U * I * cosφ, cosφ is the power factor, select 0.8; this is the three-phase power calculation formula. Single phase: P = U * I * cosφ, cosφ is the power factor The power factor is 1 for the resistive load and 0.8 for the inductive load.
- Q:What is the difference between the control cable and the compensation cable?
- 240MM copper cable can be, casing with DN150 load 473KW how current only 560A, a little do not understand, you are not wrong
WE always insists on independent research and development and takes "top quality, brand, service and reputation" as our tenet. We are continuously increasing our production capacity and export sales volume. We utilize the latest technologies, in response to the growing demands of customers through the R&D of our product lines.
1. Manufacturer Overview
|Annual Output Value
||Southeast Asia;Mid East;Domestic Market
||ISO9001, ISO14001:2004, OHSMS GB/T28001-2001, CCC
2. Manufacturer Certificates
|a) Certification Name
3. Manufacturer Capability
||70% - 80%
|No.of Employees in Trade Department
||Above 100,000 square meters
|No. of Production Lines
||OEM Service Offered; Design Service Offered
|Product Price Range