1.10-200kVA 3:3 Phase Industry UPS
2.Can parallel 8 units UPS
3.True on-line static bypass technology
Superb 10-200kVA 3:3 Phase Industry UPS,Can parallel 8 units UPS
1.True on-line static bypass technology,to provide strong overload and fault protection device
2.Internal manual maintainance bypass further improve the reliability of continuous operation of the load
Network management humanity:
1.Communicate with PC by Rs232
2.Use SNMP adapter,UPS can realize remote network management function
Optimized battery performance:
1.Intelligent battery management function
2.Automatically convert constant-current constant-voltage charging technology
1.Can parallel 8 units UPS
2.Parallel UPS units can share a battery pack
3.Non-fixed master/slave parallel
|Input Voltage||380VAC(3phsae) or 190VAC (3phase)|
|Voltage Range||304-456AVC or 152~228VAC|
|Power Factor||More than 0.97|
|Frequency||Sync to input (line mode),50Hzor 60Hz +_0.5%|
|Waveform Type||pure sinewave|
|THD||Less then 3% with linear load 110% for|
|Overload Capability||300mines/125% for 10mines for 150% for 1mine then transfer to bypass &alarm|
|Crrent Crest Ratio||3:1 (Max)|
|Overall efficiency||More than 90%|
|From inverter to Battery||0ms|
|Bypass voltage range||adjustable|
|Recharge Time||8~0hrs to 90% of capacity after full load discharge|
|LED||Battery level,utility power,inverter,bypass,fault,overload|
|LCD||Input/Output voltage,Frenquncy,Battery Voltage,Load percent,Temperature|
|interface||Rs232 SNMP (optional)|
|intelligent slot||Dry Contact/EPO/SNMP Card (optional)|
|Acoustc Niose||less than 55dB||Less than 60dB||Less than65dB||Less than 70dB|
- Q:Online power ups on the line power does not light how to do
- UPS has no normal operation, if there is normal operation, the indicator light does not shine, may be plug on the plug loose! If the UPS is not running, it may not be turned on or the power button is broken. Also may be UPS internal failure, if they can not solve, it is recommended to repair! The The Pearl River Delta region to buy, repair can find our company!
- Q:Ups power there is a way to force the closure?
- Basically, big brands of UPS have the so-called emergency shutdown function (EPO or Emergency Power Off)
The detailed operation depends on the operating instructions of individual UPS brand models.
- Q:What is the difference between DC and UPS?
- Yes, the role of the DC screen is when the power supply interruption through the dual power switch to quickly provide a reliable backup power, as well as the supply of high-voltage switch operation power.
UPS is the role of DC power into AC power supply to DCS or other devices such as computers.
- Q:Ups power can not external socket?
- Said so much to do, directly, you can pick up, but can not pick too much,
- Q:Seeking a UPS uninterruptible power supply, you can let the computer monitor printer work more than 6 hours
- Ok can support a desktop + printer + monitor for 6 hours?
Can support, MT1000S and C1KS need external battery. According to your request MT1000S external 4 100AH battery, C1KS external 6 100AH battery on it
- Q:What is the meaning of Ups in a computer room?
- A device that supplies power to the equipment after power failure
- Q:Small ups uninterruptible power supply, you can add an external battery?
- Hello, low-power UPS you want to take a large battery, then the following consequences may occur 1. battery charge dissatisfaction, the battery is not a long time to scrapped, because the small machine does not have a separate charge version, can not meet the battery charge. 2. With small and medium size batteries, may have a long charge after the discharge time, if the voltage instability, frequent power failure, the battery will be scrapped in advance. 3. Discharge when the battery trickle discharge, the battery scrapped. In summary, it is recommended not to change other models of the battery, or for UPS. Mountain has a huge MT500 charging capacity can have a long delay, you can outside the large battery. I hope my answer can help you, look forward to your praise.
- Q:UPS power supply behind the serial how to use?
- With the ups power supply with RS232 cable connected to the computer, the computer installed with the machine configuration software, you can use the computer monitoring ups power, power can be safely shut down after the computer.
- Q:Does the UPS need to be shut down every day?
- UPS does not need to be closed every day.
UPS uninterruptible power supply works as follows:
AC-DC conversion: the grid to the AC power by the autotransformer step-down, full-wave rectifier, filter into a DC voltage, the inverter circuit.
DC-AC inverter circuit: the use of high-power IGBT module full-bridge inverter circuit, with a large power margin, the output dynamic range of the output impedance is particularly small, with fast response characteristics. Due to the use of high-frequency modulation current limiting technology, and fast short-circuit protection technology, so that the inverter regardless of the supply voltage transient or load impact or short circuit, can be safe and reliable work.
- Q:UPS uninterruptible power supply wiring problem
- This can not be seen, you use a multimeter to determine whether the battery voltage is consistent with the design.
1. Manufacturer Overview
|Annual Output Value
2. Manufacturer Certificates
|a) Certification Name
3. Manufacturer Capability
|No.of Employees in Trade Department
|No. of Production Lines
|Product Price Range