Order On-line Tracking
1.DL series pumps are vertical, single suction, multistage,sectional and centrifugal ones and used for transporting pure water and the liquids below 85 C and with the physical and chemical natures similar to water's.
2.Vertically mounted, of a compact structure, low noise, small occupied land etc, features and mainly used for the water supply and the centralized heat supply system in cities.
3.The technical standard executed for this series pumps is:
JB/TQ809-89(Vertical multistage pump model and basic parameters),GB5659-85(Technical conditions for multistage centrifugal pumps).
4.Rotating direction of pump:CCW as viewed downward from the motor.
1.Model DL pump is vertically type,its suction port is located on the inlet section(lower part of pump), discharge port on the output section(upper part of pump), both are horizontally
positioned. The number of stages can be increased or decreased per the required head.There are four installation angles of 0°,90° ,180° and 270° available for selecting per different installations and uses in order to adjust the mo unting position of the discharge port (installation angle is 180° if no special note is given).
2. Major parts of the pump: inlet, middle and outlet sections,impeller, guide vane, guide vane on outlet bearing,shaft sleeve, balance drum and sleeve, conn. stand etc.
2.1 The inlet, middle and outlet sections, guide vane, guide vane on outlet section are all made of castiron and mutually form the working room of the pump.
2.2 The impeller is made of cast-iron, Liquids go in from one side along with the shaft and an axial force may exist because unequal pressures on both front and back of the impeller.Most of the force is made balanced by the balance drum while its residual is supported by the ball bearing on the upper end of the shaft.
2.3 The shaft is made of qualified carbon steel and in its middle the impeller, balance drum and shaft sleeve are mounted,which are fixed with pins and shaft sleeve nuts on the shaft to form the rotor. On one end of the shaft a lower shaft sleeve is mounted, which is fitted with the plastic bearing, and on the other the ball bearing is mounted to support the rotor and on the top of it a clutch is mounted and directly connected to the motor.
2.4 Both balance drum and sleeve form the balance device of the pump and can be replaced when worn out.
2.5 The shaft seal can not only use soft filling but also be changed with mechanical seal, when using soft filling, the shaft sleeve can be replaced when worn out and, when as the mechanical seal, the pressure water inside of the balance room is used for lubrication and cooling.
When as the filling seal, the 3/8'' flexible union on the outlet section is used through the flexible pipe to drain the water leaked from the filling body to the underground ditch to keep the place around the pump clean.
2.6 The bearing on the upper end of the pump uses molybdenum disulfide grease for lubrication
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|