Order On-line Tracking
Online Low Frequency 20~200KVA UPS Types Front Office Equipment
(208 or 380 or 400 or 480 Vac) ± 20%
/ 5 wires (3 Lines + Neutral + Ground)
|Frequency||50 or 60Hz ± 10% Autosensing|
(208 or 380 or 400 or 480 Vac) ± 20% /
5 wires (3 Lines + Neutral + Ground)
|Frequency||50 or 60Hz ± 0.1%|
|Effciency||AC / AC > 92%|
|Trandfer time||0 ms|
|Wave form||Sine wave|
|Voltage T.H.D.||< 2% with linear load< td="">|
|Crest factor||3 : 1|
|Technology||True on-line double conversion controlled by microcontroller|
|Overload recovery||Automatically transfer to UPS mode|
|Isolation transformer||Inverter mode ( bypass mode is optional )|
|Parallel connection||Parallel connection function is ready (extra PCB is not required )|
|Battery type||VRLA ( Valve Regulated Lead Acid ), not included|
|DC voltage||384 Vac||480 Vdc|
|Charging time||4 hours up to 90%|
|Battery detection||self-detect, transfer to battery mode adjustable|
Hotswappable lightning and transient surge suppressor
(In:10 Kamp, Up:1.5 Kv, I max : 20 K amp. )
output breaker, battery breaker, bypass breaker; DC fuse, fan,
redundant power supply;
temperature sensor, EPO (Emergency Power Off),
audible alarms etc.
Discharging batteries, battery charge working mode, inverter working mode,
emergency power off, manual shutdown, bypass SCR failure,
bypass sequence failure, bypass over the lilit, critical overload,
batteries exhaustion, low or high output voltage, DC fuse open,
5v power supply failure, 13.5V power supply failure, inverter overvoltage,
200% overload on each line, transfer failure, inverter voltage out of range,
over voltage between neutral and ground, UPS on bypass mode,
bypass frequency out opf range.
|Overload||125% for 10 min, 150% for 30 sec, 1000% for 16 millisencond.|
|EPO||EPO local and / or remote|
|Display||LCD, touch screen|
RS232 intellident Slot, modem, SNMP(RJ45)
(SNMP adaptive Software is supplied by the producer)
|Elevation||1.700 m.o.s. 1 without derrating|
|0℃~40℃ / < 60db @ 1.5m.< td="">|
1. Wide range of input voltage
The UPS can offer normal and stable service voltage under its input voltage range. When the input voltage is out of its range the machine will switch to battery mode automatically to keep the output power in order to protect the equipment, such as computers, ensure they will not be damaged by the over high or over low voltage, users can continue the operation of equipment for a while or save the data on computers while the power network is abnormal.
2. Wide range of AVR(Automatic voltage regulation)
In the product’s input voltage range and under 3 steps of intelligent AVR function, it can provide a stable output voltage.
3. Automatic self detection when UPS on(LED).
Before the UPS on, red, yellow, blue LED will light up two times by cycle turns, after self detection UPS switch to AC mode/battery mode or working mode.
4. Silence function
In the "battery mode", shortly press the switch to turn off the buzzer. But the battery is about to run out or the load is too heavy, the buzzer sound cannot be muted.
5. Overload protection
In the battery mode, output voltage turn down correspondingly when it is overload, after the capacity of load is lower than the rated power then output voltage will back to rated value, it ensures the UPS will not shut down by abrupt overload which caused by surging current during the computer is working and other equipment is added.
6. Short circuit protection
When the mis-operation caused the load short circuit or computer failure (such as power tube breakdown of switch) cause short circuit, the UPS will shutdown automatically for protection.
7. The low current switch
This UPS adopts low current switch to extend the service life which is longer than conventional battery and high current switch in AC current path.
8. Automatic charging
There are two charging mode, charging time is faster than ordinary charging mode, higher efficiency, and greatly prolonging the service life of the battery.
9. With a bypass output
Independent bypass output socket for external printers or scanners of computer peripherals, with surge protection of the load.
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|