Order On-line Tracking
Type: Industrial Fan Heater
Place of Origin: Hebei, China (Mainland)
Brand Name: CNBM Group
Model Number: GPKL-II
After-sales Service Provided: Engineers available to service machinery overseas
tech parameter: according to customer's needs
|Packaging Details:||1. Standard export wooden package. 2. Fumigated seaworthy wooden boxes 3. Mark as customer's requirement 4. Follow customer's packing standard.|
|Delivery Detail:||7 days|
Circulation Soft Water Cooling System ( air-water cooler)
Mode GPKL-II circulation soft water cooling system adopts closed cooling tower structure. Cooling soft water is flow in sealed water tank and cooling pipes. The inner circulation soft water is cooled by overhead fan and water-spray method using the principle absorbing heat when evaporation. The spray water circulate inside and closed cooling tower`s heat dissipation pipe, spray-water spray at pipes` surface through spray system, some heat is taken by dissipation and soft water temperature inside the pipe go down accordingly. The cut board stops water in hot air and un-evaporated water, make them flow through PVC heat exchange layer, the water in the layer is down by air, then temperature goes sown and fall down to the bottom of the tower.
Apply range: 60 kW –1200 kW induction heating power supply.
Energy saving: Low investment, small volume, compact frame, convenient installation, easy transfer and without any investment on building cooling pool and cooling tower.
Water saving: Water saving 95% compared with directly water supply cooler.
Electricity saving: Electricity saving above 90% compared with compressor cooling mode.
System adopts sealed soft water circulation, no scale, no jam.
Excellent material, advanced manufacture technics, high heat dissipation efficiency. The equipments dissipation parts adopts high quality of brass & aluminum compound pipe with advanced manufacture technics, brass outer pipe connects hydrophile aluminum platinum fin board in expanding joint mode. Such structure has very large heat dissipation area, high dissipation efficiency, its dissipation ability is far more better than pure aluminum pipe, steel pipe and steel & aluminum fin board.
Best cooling effect due to wind cooling and spray water complex cooling mode. Low temperature in winter, single air cooling can meet production demand, no need to run spray; high temperature in summer, also high water temperature, wind cooling plus spray mode can be used which guarantee some key parts wont damage due to over high water temperature in summer such as SCR, capacitor, reactor, induction coil etc. Therefore prolong using life-span of equipment.
Design as customer's specific demand
Onsite supporting engineer team
Technical consult and guiding
Using environment for H.F. welder
1. Environment requirements
1.1 Indoor installation, heating equipment and heating furnace should earthing well, earthing wire color must be obviously different form control wires, its section area >4mm2, earthing resistance should be no more than 4Ω.
1.2 Height above sea level should be no more than 1000 meters, or else reduce rated value for using.
1.3 Surroundings temperature: 5~40℃.
1.4 Air relative humidity should be no more than 85%.
1.5 No severe vibration, no conductive dust, no various causticity gas and explosion gas.
1.6 Installation gradient should be less than 5°.
1.7 Installed on excellent ventilation situations.
2. Power net requirements
2.1 Power net voltage is sine wave, harmonics distortion should be no more than 5%.
2.2 Imbalance degree between 3-phase voltage should be less than ±5%.
2.3 Power net input voltage is line voltage AC 380V, the constant fluctuation range should be less than ±10%, 2.4 power net frequency variation should be no more than ±2% (i.e. between 49 ~ 51Hz).
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|