Order On-line Tracking
Copper/Aluminium conductor , XLPE/PVC insulation , PVC/LSZH outer sheath power cable.
Voltage rated: 0.6/1KV
Temperature: Not exceed 90°C
Bending radius: Single cord 20*OD
Multi cords 15*OD
Rated Uo/U is 600/1000V and 450/750V.
Allowed continuous working temperature of conductor is 90 .
Installation temperature of cables should be no less than 0 .Allowed bending radius should be no less
Maxi mum temperature of conductor (the longest continuous time should be no more than 5s) should be
no more than 250 .
Conductor construction and D.C.Resistance should be in accordance with Table 3
Insulated core can be identified with different colors and different numbers. The nominal
thickness o f insulation i s 0.7mm. The thinnest place o f insulation should be no less than
90%-0.1mm of nominal value.
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|