Online UPS 1-3KVA
XPC 1-3KVA series UPS is an economical, full featured UPS that delivers cost-effective power protection in a compact package. It adopts advanced MCU technology, delivers high reliability and performance, and has intelligent battery management system. XPC 1-3KVA series UPS is best enterprise-class choice for crucial load.
Green and Save Energy
IGBT rectifier offers an input power factor more than 0.99, input THD less than 3%. Therefore it does not pollute the input utility
supply or other devices which share the same utility source.
Wide Input voltage window and auto detection of input frequency function adaptive to adverse utility power grid enviroment.
Extra wige range of input voltage and frequency is suitable for low quality power grid environment 。Complete fault protection
functions, overload, short circuit, overvoltage, under voltage, over temperature protections.Strong overload capability: 5min for 130% rated load and 60s for 150% rated load Intelligent battery management charging/discharging interval time and keep battery long life.
User Friendly Display and Communication
The LED mimic diagram gives clear indication of real-time status and power flow through the UPS.The large LCD graphical display provides an array of performance parameters, fault information and 220historical event log that are useful for troubleshooting.
The system provides RS232 signals for remote monitoring, and SNMP (optional) for web-based monitoring.
Friendly LED display (standard) or LCD display (optional)
Four kinds of optional cards to provide network communication functions (support dry contact, RS232, RS485 and TCP/IP
Ideally Suited For:
Small routers and bridges
Other sensitive electronics
|MODEL||XPC 1101||XPC 1101L||XPC 1102||XPC 1102L||XPC 1103||XPC 1103L|
|Input Voltage||(110±5 to 296±5)VAC|
|Input Frequency||(45±0.5 to 55±0.5)Hz|
|Bypass voltage||(80±5 to 286±5)VAC|
|Output Power Factor||0.8|
|Output Frenqency||45Hz～55Hz, same with utility power; <45Hz and >55Hz, lock 50Hz|
|THD||THD<3% (linear load)；THD<5% (Non-linear)|
|Transfer Time||Normal to battery mode: 0ms|
Between Battery modeand normal mode: <4ms
|Overload Capability||105±5%≤Load≤150±5%：30s to bypass;|
>150±5%：300ms to bypass;
|Battery Type||7AH/12V× 3pcs||7AH/12V× 6pcs||7AH/12V× 8pcs|
|Backup Time (Full Load)||>5min(depends on battery capacity for L type)|
|Charging Current||1A/3A、4A、5A、6A、7A setable(L type)|
|Communication||RS-232 + Intelligent Slot|
|Restart||After turing off due to cut off voltage of battery, UPS will restart|
when voltage is in (170±5~286±5Vac) and freqency is in (46~54Hz).
|Noise (1m front)||<45dBA||<50dBA|
|Operation Temperature||0°C to 40°C|
|Storage Temperature||-40°C to 50°C|
|Altitude||<1000m，>1000m derated1% per 100m|
|* Specification is subject to change without prior notice.|
- Q:Low voltage, computer restart UPS power can use it?
- UPS can solve this problem,UPS function is the voltage is too low, automatically switch to UPS batteries, this is instantaneous, will not affect the equipment reset, otherwise the power will restart, UPS still sell out, I have been using. However, the outage time can not be too long. Usually in about 20 minutes.The role of voltage regulator is still small, after all, there is no standby battery, it is impossible to compare with UPS. As long as the power is off or the voltage is too low, it stops naturally,
- Q:How do you calculate the power supply time of UPS?
- There are usually two ways to calculate a UPS battery:First, constant current mode calculation:According to the principle of conservation of energy, the following formula is used:C = (PL * T) / (Vbat * n * K)The C battery capacity, (Ah) PL uninterruptible power output power (W); T (H) - battery backup time;Vbat battery voltage (Vdc) is UPS battery inverter efficiency (0.90-0.95, according to the selected models).K - battery discharge efficiency (coefficient).
- Q:What is the function of UPS?
- UPS (Uninterruptible Power System/Uninterruptible Power Supply), namely, uninterruptible power supply, the battery is (for maintenance free lead-acid batteries) connected with the host, the host through the inverter module circuit of the direct current into power system equipment.
- Q:What's the difference between UPS and EPS?
- The UPS object is the power supply of computer and network equipment, load characteristics (input power factor) is not very different, so the national standard UPS and EPS power supply output power because the 0.8. object is power protection and fire safety, load properties for inductive and capacitive and rectifier type nonlinear load and the power factor, the output cannot be set to 0.8 (EPS GB will provide its value), and some only work load is stopped after power, thus EPS can provide high impact current, EPS needs better output dynamic characteristic, anti overload ability. Therefore EPS and UPS technology to design the index distribution of each component is different.
- Q:What is the name of the device that provides the server with power?
- UPS is the abbreviation of uninterruptible power system, which is an important external equipment to provide continuous, stable and uninterrupted power supply.
- Q:Does UPS have the effect of stabilizing?
- The power supply has the ability of anti surge current, UPS also has, but the main function of UPS is that the backup power supply, power outages continue to provide short time power for the computer, so that the computer can not save the finished files after shutdown.As you say, using UPS is not to solve the problem, should be reflected to the local power supply department, so that they solve.
- Q:What are the UPS power supplies and its uses and features?
- UPS power supplyNetwork equipment and communication equipment precision is not allowed with intermittent power, to the server as the core network center to be equipped with UPS is self-evident, even an ordinary computer, the use of three months after the data file has exceeded the value of software and hardware, so as to prevent data loss is also equipped with UPS is a must.According to IDC statistics, all 45% computer fault is caused by power supply problems; in China, the number of big city blackout for an average of 0.5 times per month, medium city is 2 times / month, a small city or town is 4 times per month, at least nine kinds of problems: power grid, lightning surge, frequency, peak the rate of oscillation, voltage mutation, voltage fluctuation, frequency drift, voltage sag, pulse interference; so from the perspective of improving power quality to a computer equipped with a UPS is very necessary.
- Q:UPS technical index
- How much power should I have with my UPS?We must first determine your equipment is much power in general, ordinary PC or IPC power is about 200W, apple at about 300W server between 300W and 600W, the power value of other equipment can refer to the equipment manual.Secondly, should understand the power rating of the UPS has two methods: apparent power (VA) and the actual output power (W), due to the reactive power are so made the difference, the relationship between conversion: apparent power power factor * = actual output powerBackup, online interactive power factor between 0.5 and 0.7, the online power factor is generally 0.8.When UPS is allocated to the equipment, the actual output power of UPS should be matched. Some dealers intentionally or unintentionally confuse (VA) and (W), which should be brought to the attention of the user.
- Q:What is the difference between inverters and UPS?
- The term "voltage regulator" is also mentioned here. The voltage regulator can maintain the unstable power supply at a fixed voltage by means of a voltage stabilizing device, which is very beneficial to the normal use of the electric appliance.In civil use, voltage regulators are widely used, such as refrigerators and air conditioners, and many users install high-power regulators on the total incoming line, which makes all electrical appliances protected. We know that, especially after the power failure is resumed, the voltage will have an overload peak and the instantaneous voltage is too high. This is the reason why most of the electrical appliances are damaged.
- Q:UPS uninterrupted power supply, how long can you extend the power supply?
- UPS standby time is UPS by the energy storage device is decided, UPS now generally used sealed maintenance free lead-acid battery as energy storage battery capacity by the number of ampere hour (AH) "this index, which means the discharge in accordance with the provisions of the current time. The same voltage of the battery, when a large number of large capacity; the same number of ampere hour battery, voltage high voltage and large capacity, usually with ah. Said the capacity of the battery, such as 12V/7AH, 12V/24AH, 12V/65AH, 12V/100AH.
1. Manufacturer Overview
|Annual Output Value
2. Manufacturer Certificates
|a) Certification Name
3. Manufacturer Capability
|No.of Employees in Trade Department
|No. of Production Lines
|Product Price Range