Order On-line Tracking
JDCF-138GYW is a product which have 4 windings and oil insulation voltage transformer.The product conform to the follows national requirement:GB1207-1997 phase <voltage transformer>,GB7354-85<Transofrmer Measurement of Partial Discharge>,GB311.1.19 <Insulation Coordination of High Voltage Transformation>,the international electric stand IEC186 or IEC60044 phase <Voltage Transformer> .This type product is used for electric energy measurement and relay protection in 145KV power system.
1.2 Structural characteristics
This type of voltage product has a cascading insulation structure.Iron corn is the " "shape and overlying by silicon steel sheet.Two iron corn were supported by shelf which mad by low dielectric phonetic paper board.Four coil nest is in the two iron com,The coil reelwith balance winding.measuring secondary winding,protective secondary winding,residual voltage winding.The primary winding was made by unifilar enameled wire and have four class,The upper extreme(A extreme) is all insulation.The lower extreme(N extreme)joint to expansion equipment plinth by push ring.There are three oil mark(+45oC,+20oC,-25oC) beside the expansion equipment.The plinth support the whole product,the terminal of measuring secondary winding,protective secondary winding,residual voltage winding,primary winding bring out formthe plinth.The primary winding N extreme joint to the plinth by joint panel which will be convenient to the test and installation.
1.3 Product mark
the primary winding is A and N,the measuring secondary winding is 1a,1n.the proctive secondary winding is 2a,2n.the residual voltage winding is da,dn.
2.1 Am bient temperature:
maximum air temperature:+45oC
minimum air temperature:-25oC
maximum average air temperature:+30oC
2.3 minimum creepage distance:3520mm
2.4 atmosphere condition:have o serious pollution in atmosphere,the pollution grade is Ⅲ.
2.5 earthing manner:neutral point joint the earthing efficiently.
The rated value and requirement
3.1 the rated voltage
a.the maximum voltage:145kv
b.the rated primary voltage:138000/V
c.the rated voltage of measuring and protective winding:115/V
d.the rated voltage of residual voltage winding:115V
3.2 the rated frequency:50HZ
3.3 phase:single phase
Operation and maintenance
4.1 Before the installation,inspect the sealed place and welding.It has oil leakage and oil surface is normal,If not,it should oiling the same type oil.
4.2 The oil drawing is from the bottom and its electric intensity is not more than 50KV
4.3 The secondary should not open circuit in the product operation.
4.4 The product should veiled when it storage Before the operatio,it should not be sun or rain.The product shoue be packed.
No tesdge for ordering
a.type of product
b.the rated voltage of each winding
c.accuracy class and rated load
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|