Characteristic: It has characteristics low noise, long life and high efficiency.
Shaft seal: This series of pump adopt mechanical sealing. It also adopts the packing seal according to the requirement of customer.
Temperature: The max environment temperature is 50 °C and the max use temperature is 80 °C.
( If you are looking for arc gear pump used in ships, just need it -- LYB Vertical Arc Gear Pump. )
LYB arc gear pump
LYB VERTICAL ARC GEAR PUMP
Environmental temperature: <50°c
Use temperature: <80°c
GL, ABS, BV, CE, CNV etc.
About 25~40 days according to quantity.
GL, ABS,BV, CE, 3C, ISO9001-2000, GJB9001A-2001
Standard export carton or plywood case. (By sea or by air)
Within 25 working days after confirm orther
LYB arc gear pump
Outline and Installation diagram
Rated pressure: 0.6Mpa
All Products can be matched with different motors as customer's requirment
Send a message to us:
Q:Pneumatic diaphragm pump compressed air pressure is 4 kg, the discharge pressure is how big?
Have to know the ratio, pneumatic pump, if high pressure, you can have 2:1,3:1
Q:What does "dual purpose" of water pump mean? Please expert advice
In order to ensure safe and continuous operation, three pumps usually need two units and run one standby.Precautions for using pumps1, if there is any small water pump failure, remember not to work. If the pump shaft packing end wear should be added in time, if you continue to use the water pump will leak. The direct effect of this is the increased energy consumption of the motor, which will damage the impeller.
Q:Why is the flow of the pump too small will occur cavitation phenomenon?
This is because the impeller of the centrifugal pump rotating speed under the drive of the prime mover, when the valve opening decreases, flow rate is too low, can not be taken away by the friction heat generated by the impeller and the liquid completely, make the temperature of the liquid inside the pump. Thus causing liquid vaporization, forming cavitation. Especially in the power plant, the boiler feed pump is more remarkable. Therefore, when throttling regulation, we should set up recirculation system, increase the output flow of the pump to prevent cavitation. When the feed water rate is reduced to 1/3 of the maximum flow rate, the recirculating gate shall be opened so that the flow of the feed pump will be increased properly to ensure that the liquid temperature in the feed pump does not rise.
Q:Roots pump and dry pumpRecently, the work involved in the vacuum pump, do not understand this, is a ads602 vacuum pump
Here the roots pump and dry pump must be used, because the roots pump is not used alone, and must be a stage vacuum pump (pre vacuum pump can be dry pump, water ring vacuum pump and rotary vane vacuum pump can be, you here with dry pump series)
Q:What is the minimum continuous flow of a pump?
At'-- the allowable temperature rise of pumping medium,C- pumping medium specific heat, kj/ (kg DEG C);Ho- off dead center lift, M.Minimum continuous flow minimum continuous stable flow and minimum continuous thermal flow and the maximum value in the selection, or use the pump process, the minimum continuous flow process requirements must be greater than the minimum flow rate of the pump, otherwise it will cause the pump cavitation, vibration and noise, so that the pump parts damaged. If the minimum continuous flow the pump can not meet the minimum requirement's process, can install the bypass reflux device or reflux system in the pump pipeline, to ensure that the minimum continuous flow pump.
Q:The suction pump has a nominal suction range of 30 metersHow deep can a well be sucked?Well, sixteen meters,
Vacuum pump plus form must not reach a standard atmospheric pressure vacuum, so the general can absorb 8 meters is very good, and the self suction pump itself and loss, the horizontal self-priming pump can suck on basic 4~6 meters is very good, self-priming pump. Suction lift of 30 meters is purely in the Mongolian people, does not comply with the laws of nature, obvious anti science.
Q:Any center of the pump
Alignment methods and requirements:1, check two feeler dial gauge or flange coupling the parallelism, usually with clearance between the both ends of the side instead of difference, in the circumferential direction every 900 measure, the maximum and minimum gap gap difference (Ab) less than or equal to 0.3 mm.2, the coupling flanges outside the park up and down, left and right four position to check whether they are in the same line, C less than or equal to 0.1 mm.When looking for a positive C, it will affect (a - b), finding the right (a - b) will affect the C, to balance each other. It's easier for an unskilled comrade to find C (a - b) first, and then find a positive one. Through the adjustment of the motor at the foot of the gasket thickness (Ab) and meet the requirements of C.Check the inlet and outlet piping before alignment. Make sure the weight of the inlet and outlet pipe does not exert force or torque on the pump. When looking for, should also pay attention to eliminate the pump rotor movement, so as to avoid the end gap error. If checked after the pump is working, it should be carried out under cold condition.It is important to draw attention to the fact that the pump set of the complete set of factory is only rough looking (checked with a ruler) when it is shipped. It may cause displacement when it is transported.
Q:Constant pressure pump working principle
The pressure loss is borne by the valve. Constant pressure pumps generally do not export direct load, unless you need this load response is very fast, then the maximum displacement of the pump work, so as to ensure the rapid response of the load.
Q:How to calculate the motor power of metering pump?
Two Hydraulic power, metering pump rated flow (L/H) X, maximum pressure (Barg) / 36000 = kw
Q:Why should I pump the pump before starting the centrifugal pump?
Only centrifugal water can be pumped out of the centrifugal blade to generate negative energy at the entrance. There is no water diversion. Only the negative pressure produced by the air is too low to absorb the well water.Water pump has been pumped, centrifugal pump or can not start normally, mostly because of the water pipes and air