Order On-line Tracking
The surface of conductor should be bright and clean no grease, no burr or bulge or faulted wire to damage the insulation.Every conductor coat with an isolated layer made from appropriated material.
The nominal value of the insulation thickness shall comply with IEC60227-7. The average value of insulation thickness should be no less than nominal value, and the thinnest part should be no less than 90% -1mm of nominal value.
Insulation adopts XLPE, whose property should comply with provisions in IEC60502-1. The insulation should be rapped on conductor tightly and easy to peel without damaging the insulation, conductor and coating. The surface of the insulation should be flat and color evenly
• The lowest temperature that cable could work should not lower than-300C.
• Max temperature is 150 0C for short period ( 2h maximum duration each time).
Ambient air temperature: Perennial mean temperature: 10℃
Extreme high temperature: 50℃
Extreme low temperature: -42℃
Average relative humidity: normal value for accumulated year: 80%
Earthquake Proof: Horizontal acceleration: 0.2g
Normal acceleration: 0.1g
Range of Laying:
Cables mainly lay in the cabin of fan, where machinery oil may leak or overflow.
Rated Voltage U0/U: 300/500V
Continues operating temperature: Flexible: -5～+90℃
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|