Single Conductor Stranded Wire H05V-U, H07V-U, H07V-R, BS6004 6491X, BV, BVR
The cable has the advantage high mechanical strength,good ambient stress resistance,good electrical properties and anti-Chemical corrosion. It applies to electrical power transmission and distribution lines with AC rated Voltage up to 450/750V. The cable is for general purpose, as building wire for power, lighting and control wire to electrical appliances, suitable for use in conduit and for fixed, protected installation.
Rated voltage: 300/500V,450/750V
Standard applied: IEC 60227, BS 6004, VDE 0281, GB/T 5023, JB/T8734
Max. working temp.:70°C,can be 90°C,105°C per requirement
Conductor: Class 1/2 plain annealed copper wires, solid or stranded.
Insulation: PVC material
Cores: 1 cores
Cross section area: 0.5~630sqmm
Color: Brown, Grey, Black, Blue, Green/Yellow or others on request
Packing: 100 meters per roll or as per requirement
OEM can be available
BDK cable has very good sales over the world, enjoying a very good reputation based on top quality and most competitive price and best service.
Flame retardant or fire resistance or Low Smoking and Halogen free or other property can be available
|H07V-R H07V-U H05V-R H05V-U BY 227IEC01/05 equivalent to VDE 0281 BS6004|
|Cross section (mm2) ||Conductor construction (No/mm) ||Insulation thickness (mm) ||Overall diameter max (mm) ||Min insulation|
|Weight approx (Kg/Km) |
|1x0.5 ||1/0.80 ||0.6||2.4||0.015||8|
|1x0.75 ||7/0.97 ||0.6||2.8||0.012||11|
|1x0.75 ||1/0.97 ||0.6||2.6||0.012||11|
|1x1.0 ||7/0.43 ||0.6||3||14|
|1x1.0 ||1/1.13 ||0.6||2.8||0.011||14|
|1x1.5 ||7/0.52 ||0.7||3.4||0.01||21|
|1x1.5 ||1x1.38 ||0.7||3.3||0.011||20|
|1x2.5 ||7/0.67 ||0.8||4.2||0.009||32|
|1x2.5 ||1x1.78 ||0.8||3.9||0.01||31|
|1x4 ||7/0.85 ||0.8||4.8||0.0077||45|
|1x4 ||1/2.25 ||0.8||4.4||0.0085||45|
|1x6 ||7/1.04 ||0.8||5.4||0.0065||65|
|1x6 ||1/2.76 ||0.8||4.9||0.007||65|
|1x10 ||7/1.35 ||1||6.8||0.0065||110|
|1x10 ||1/3.57 ||1||6.4||0.007||110|
|1x16 ||7/1.70 ||1||8||0.005||165|
|1x25 ||7/2.14 ||1.2||9.8||0.005||264|
|1x35 ||7/2.52 ||1.2||11||0.004||360|
|1x50 ||19/1.78 ||1.4||13||0.0045||490|
|1x70 ||19/2.14 ||1.4||15||0.0035||685|
|1x95 ||19/2.52 ||1.6||17.5||0.0035||946|
|1x120 ||37/2.03 ||1.6||19||0.0032||1181|
|1x150 ||37/2.25 ||1.8||21||0.0032||1453|
|1x185 ||37/2.52 ||2||23.5||0.0032||1821|
|1x240 ||61/2.24 ||2.2||26.5||0.0032||2383|
|1x300 ||61/2.50 ||2.4||29.5||0.003||2983|
|1x400 ||61/2.85 ||2.6||33.5||0.0028||3800|
Main manufacturing procedure
1. Copper wire drawing and annealing
2. Copper wire stranding
3. Outer sheath extruding and labeling
Main Quality Inspection Equipment
Sparker tester,Heating aging Chamber,High resistance machine, Oxygen index equipment, Partial discharge inspection instruments, Fireproof testing device,High-power voltage withstand tester,No-rotor Vulkameter,Pull tester,Analytical balance,Direct current bridge,Plastic tester,Projector, Punch machine,Cross-linked cutting machine,etc.
- Q:Building electrical power equipment in the dark pipe is threading or wearing a cable?
- Do you say the wire protection tube? If the commonly used plastic pipe has Φ. Φ. Φ. Φ32. Also on the metal wire tube with G15G20G25G32G40G50
- Q:The first PC installed, how to install the order and how to take a good line.
- 4 square of the national standard line is certainly enough, if the non-standard line that would be 6 square
- Q:Power supply 6PIN (graphics card) with CPU 8PIN will be a problem?
- No, the disk will lead to heat accumulation, the impact of wire cooling, serious will burn the wire, especially in the maximum current carrying capacity when the wire is more obvious, so the use of wire tray up to no more than 1/2 rated current, "The inside of the two lines of the current direction is always the opposite can be offset each other to produce the electromagnetic effect" This is very right, the use of wire tray will not increase the wire impedance, but not a single wire, must be the same Two of the circuits at the same time disk up. Wire: the wire is made of one or several soft wires, the outer package is soft and soft; the cable is made of one or several insulated packets, and the outer layer is covered with a tough outer layer of metal or rubber. Cables and wires are generally made up of three parts: the core wire, the insulating sheath, and the protective sheath. Commonly used cable features are as follows: CEF - EPR insulated neoprene jacket, marine flame retardant power cable. CVV - PVC insulated, PVC sheathed marine flame retardant power cable. OVC cable commonly used BV, BX, RV, RVV series of wires, including: BV - copper core PVC insulated wire, long-term allowable temperature 65 ℃, the minimum temperature -15 ℃, working voltage AC 500V, DC 1000V, fixed laying In the room, the outside can be deposited can also be deposited. BX - copper core rubber insulated wire, the maximum temperature of 65 ℃, apply to the room. RV - PVC insulated single-core cord, the maximum temperature of 65 ℃, the lowest temperature -15 ℃, 250V AC voltage, DC 500V, for the internal wiring equipment and equipment. RVV - Copper core PVC insulated and sheathed flexible wire, allowing long-term working temperature of 105 ℃, working voltage AC 500V, DC 1000V, for wet, mechanical protection requirements, often moving and bending occasions.
- Q:How many squares of wires are used in ten
- Certainly not a drag 4 infrared head .2A12V power supply to use 4 or a 10-amp central power supply (night infrared light to open the power to be good enough) a 2A12V power to take 4 words then infrared camera Will be insufficient power supply,
- Q:In the elevator, on the installation of video lines and telephone lines to go and installation tutorials? (6)
- Formal cable itself has a waterproof function, as long as the cable at the terminal (such as the junction box) using a sealed connector, do a good job on the seal, there is no need to superfluous. If you need to protect the cable, using PVC electrical insulation tube can be.
- Q:I want to turn my computer into a TV, how do I get it?
- The plug to face their own, the right side of the line of fire, the left side of the zero line, for the protection of ground
- Q:How can improve the speed, configuration, what can be under what, to move the network line to say
- 27KW * 1.5A / KW = 40.5A (per phase current) 36KW * 1.5A / KW = 54A (each phase current) 10 square line maximum withstand current 40A, switch to 3 * 16 +2 * 10 cable, With M1-63A / . contactor replaced by CJX2-. with two 10 square lines and parallel line, 25-ping line of safe current in the 80 or so, with two small, water heater lead or replaced It, if only temporary can also be used for a long time or for a washing machine and the energy of the energy-saving lamps add up to 200 watts, can be ignored.
- Q:How to distinguish between high and low voltage power cables
- Control cable transmission is the signal, the current is relatively small (that is, the conductor cross-section is small), the voltage range is narrow (450/750 ~ 10KV), cable core number is more, from 2 core ~ 61 core, or even more Control cable also uses a variety of core structure, shielding and other measures to obtain a satisfactory electromagnetic compatibility
- Q:Why some cable tray to spray, what is the role?
- General cable tray production are customized 30 meters, 50 meters. And is the rubber and plastic line, the wolf cable type can be based on the requirements around the different meters, and is the national standard rubber cable.
- Q:It is not necessary to draw a set of video lines from the monitor interface
- Do parts, like car accessories ah, but the requirements of physical mathematics is better. Do not worry about employment
1. Manufacturer Overview
|Annual Output Value
2. Manufacturer Certificates
|a) Certification Name
3. Manufacturer Capability
|No.of Employees in Trade Department
|No. of Production Lines
|Product Price Range