Order On-line Tracking
This products is apply to the power distribution system of residence, office building, hotel, hospital, shopping mall, factory and so on.
2、Type and Specification
1 core：main cable 10～500；branch cable 6～240；
Cable dc resistance should comply with GB/T 3956-2008.
3. Operational Performance
a. Cable conductor allowed long-term working temperature not exceeding 90 ℃.
When short circuit happened (the duration no longer than 5 seconds), the maximum temperature of cable conductor is not exceeding 250℃.
b. When laying cable, the ambient temperature should not be lower than 0℃,if not the cable need to be preheated. The bending radius of three cores unarmored cable should not be less than 15 times of outer diameter of cable, 20 times for armored cable.
c. Cable DC resistance should comply with GB/T 3956-2008.
d. The laying of cable is not limited by the level drops.
e. AC voltage withstand test: 3.5kV/5min no breakdown.
4、Cable structure diagram
1. Manufacturer Overview
|Annual Output Value|
2. Manufacturer Certificates
|a) Certification Name|
3. Manufacturer Capability
|No.of Employees in Trade Department|
|No. of Production Lines|
|Product Price Range|